T Link - Refer to Fuse Link, Type T.
Tap - A connection brought out of the winding at some point between its extremities, usually to permit changing the voltage or current ratio.
TCC (Time Current Curve) - TCCs are a series of points plotted in a curve on log-log paper describing the current-time reacting characteristics of a current interrupting device. TCCs are a tool used by engineers to determine coordination and correlation of devices.
Temperature Rise - The temperatures increase over ambient due to load.
Temporary Overvoltage (TOV) - A temporary overvoltage is define as an excursion of power frequency voltage above the normal line-to-ground value. Such excursions are of variable magnitude and duration.
Three Phase Power - Three separate outputs from a single source. There is a phase difference of 120° between any two of the three voltages and currents.
Time Current Curves (TCC) - A series of points plotted in a curve on log-log paper describing the current-time reacting characteristics of a current interrupting device; a tool used by engineers to determine coordination and correlation of devices.
Time to Impulse Sparkover - The time between virtual zero of the voltage impulse causing sparkover and the point on the voltage wave at which sparkover occurs.
Tracking - Irreversible degradation of surface material from the formation of conductive carbonized paths.
Transformer - A static electrical device which by electromagnetic induction transfers electrical energy from one circuit to another circuit usually with changed values of voltage and current in the process.
Conventional - A transformer that has no protective equipment (fuses, breakers, arresters). They are used when the protective equipment is provided by a fuse cutout attached to the pole beside the transformer.
CSP (Completely Self-Protected) - A transformer that contains an internal breaker, an expulsion fuse and an arrester.
Dead Front - A transformer that has bushing wells and inserts or one-piece bushings used with elbows. The operator is not exposed to live parts.
Live Front - A transformer that has porcelain bushings with one or two hole spades or eyebolts from primary terminations. The operator is exposed to live parts.
Padmount - A transformer designed for mounting on a concrete pad with underground connecting cables.
Polemount - A transformer designed for mounting on a pole with overhead connecting lines.
Transient - A high amplitude, short duration pulse superimposed on the normal voltage.
Transient Response - The ability of a circuit to faithfully reproduce a transient applied to its input.
Turn Ratio - The ratio of the number of turns in the high voltage winding to that in the low voltage winding.